I only see BACnet objects for one CT. Why?
When the meter is configured, it must have at least one LOAD defined. Each load is represented as its own BACnet virtual device instance (VDI). Each VDI has up to three CT’s available to be configured and accessed via BACnet. In addition to the LOAD VDI, the power meter has its own device instance root device with a BACnet object list. The BACnet object list is available on the meter itself via the web portal and also by navigating to Setra www.Setra.com and going to the power meter product page. Note – when you interrogate the root device instance, no CTs will be available. CTs are only available under the LOAD VDI.